Ecosoft MO-9 is a fully automated 9…12 m3/h reverse osmosis system. The equipment includes Grundfos high pressure pump, Dow Filmtec™ extra low energy membranes, Danfoss automated valves and Honeywell flow control valves.
The RO system is equipped with a controller and most necessary instrumentation. A range of options is available on request. Ecosoft RO systems offer great value in the following applications.
Less boiler blowdown compared to ion
exchange softened water
Enhanced rejection of silica, boron, ammonia,
and other impurities compared to other
Consistent rejection of pyrogens and toxic
Enhanced Dow Filmtec™ membranes and
raw water blending available optionally
Purified water is requisite for most processes
in chemical industry
Prevention of scaling and corrosion
due to hardness and other impurities
Used to obtain any grade of water for metal
Prevention of stains and scale on glass surfaces,
lower detergent usage
Used to obtain any grade of water for textile
Heavy duty Dow Filmtec™ membranes for
problem water with nitrate, ammonia, high TOC,
high TDS available as option
Demineralized water is most suitable for both
plants and irrigation systems
Optional raw water blending allows to fine tune
TDS, hardness, and alkalinity to specific
RO water meets the EC Drinking Water
Directive and protects pipes and valves against
scaling, clogging and corrosion
Prevention of stains and scale, cleaner
wash/laundry, lower detergent usage
Dow Filmtec™ XLE membranes and Grundfos®
pumps offer lowest energy use per m3 permeate
Flow capacity 1
Inlet pressure of water 2
Influent flow rate during service
Influent flow rate during rinse
Connection port sizes:
— feed water
Dimensions (Height x Width x Depth)
Feed water requirements
— Total Dissolved Solids
— Hydrogen Sulfide
— Silt Density Index
2 stable pressure (+/- 0.5 bar) in the specified range is required for steady operation of the system
Components of the system:
Dow Filmtec™ XLE membranes
Grundfos high pressure pump
Danfoss motorized valves
Permeate conductivity sensor
Low and high pressure switches
Vibration resistant pressure gauges and rotameters
Powder coated steel frame
Dow Filmtec™ ECO PRO and BW30HRLE membranes for problem water
Membrane rinse with permeate
Raw water blending
Feed water goes through sediment prefilters to remove particles.
If using antiscalant for hard water then it is injected before the prefilters, so the chemical is mixed with water more thoroughly.
High pressure pump feeds the prefiltered water into the membrane array. Inside the membranes, feed water is separated into purified water (permeate) and brine with retained impurities (concentrate).
Ecosoft RO systems feature built-in concentrate recycle, sending part of the concentrate back to the pump. Recycle flow control and drain flow control work to sustain the operating pressure and the recycle/waste ratio.
Operating pressure is variable within allowed range. Higher pressure produces higher permeate flow rate and/or recovery. Proper operating pressure and recycle/waste must be set up during commissioning.
Ecosoft RO system runs in a completely automated fashion. The system stops to standby when pure water tank is full. Automated membrane rinse occurs every time before standby, with preprogrammed intervals during standby and service.
If any of below conditions occur, the system switches off and displays failure alert:
low feed water pressure
high operating pressure
high permeate conductivity
phase or voltage failure
changing out expendable filters in pre-filter housings
chemical clean (CIP) the RO membranes when signs of membrane scaling or fouling arise; those include lower permeate flow rate or higher permeate conductivity 10% or more; normally, CIP lasts a few months before another CIP is required
if CIP fails to restore membrane flux, the membrane elements need to be replaced;
whenever an extended downtime is to happen, the membranes should be rinsed and soaked in preservative solution
Carefully read the instruction before operating the unit.
Only use piping of equal or larger diameter than the RO system's inlet and outlet ports. Avoid long runs of small diameter pipe.
Only use equal or larger diameter point-of-entry filters to provide maximum influent water flow rate. 2,5×10 size filters only have up to 1-2 m³/h capacity (5-10 gpm) and should not be used for this Ecosoft RO system.
Membranes are shipped in original packaging and must be installed before operating the system. O-ring seals on the membranes must be on the feed water side of the pressure vessel.
Remove plastic wraps from filters before installing them in pre-filter housings.
Make sure feed water is supplied to the system at required pressure before starting up the system.
Check Lovato protection relay when connecting power to the cabinet. Red light or flashing green light signals phase failure or abnormal voltage conditions as per instruction.
Do not use brass, iron, or copper pipe for permeate plumbing.
During first run, concentrate flow rate, recycle flow rate, and the operating pressure must be adjusted with the flow control valves. The operating pressure must not exceed 12 bar. The ratio of permeate flow rate to drain flow rate must not exceed 0.75.
It is advisable to supply influent water using a feed water tank and pump, and to deliver permeate using permeate tank and pump.