Ecosoft MO-3 is a fully automated 3…4 m3/h reverse osmosis system. It is pre-engineered and pre-fabricated at the Ecosoft factory for turnkey delivery, installation, and commissioning at your site. The product water is delivered in continuous 24-hour service. System maintenance (see Operation and Maintenance tab) will be required every few weeks in most operating environments.
The main equipment includes:
— Grundfos® high pressure pump
— Dow Filmtec™ membranes
— Ecosoft process controller
— Pressure vessels, valves, and other hardware from EU vendors
Most necessary instrumentation is built-in. Additional plug-in equipment, membranes, and consumables are linked at the bottom of the page. Feel free to reach us out for more detail on this product!
Ecosoft RO systems offer great value in the following applications.
Less boiler blowdown compared to ion
exchange softened water
Enhanced rejection of silica, boron, ammonia,
and other impurities compared to other
Consistent rejection of pyrogens and toxic
Enhanced Dow Filmtec™ membranes and
raw water blending available optionally
Purified water is requisite for most processes
in chemical industry
Prevention of scaling and corrosion
due to hardness and other impurities
Used to obtain any grade of water for metal
Prevention of stains and scale on glass surfaces,
lower detergent usage
Used to obtain any grade of water for textile
Heavy duty Dow Filmtec™ membranes for
problem water with nitrate, ammonia, high TOC,
high TDS available as option
Demineralized water is most suitable for both
plants and irrigation systems
Optional raw water blending allows to fine tune
TDS, hardness, and alkalinity to specific
RO water meets the EC Drinking Water
Directive and protects pipes and valves against
scaling, clogging and corrosion
Prevention of stains and scale, cleaner
wash/laundry, lower detergent usage
Dow Filmtec™ XLE membranes and Grundfos®
pumps offer lowest energy use per m3 permeate
Influent flow rate (service)
Influent flow rate (rinse)
Inlet pressure of water
3 × 380 V, 50 Hz
1 depends on feed water TDS, temperature, and permeate recovery — see graph on the right
Grundfos® CR 10-12 pump
Dimensions (width × depth × height):
FRP membrane housings
— RO system
BB20 sediment prefilter
— shipping crate
— RO system with membranes
Electrical panel with process controller
— plus shipping crate
Connection port sizes:
Instruments (switches, gauges, meters)
Membrane elements Filmtec XLE-440
Feed water requirements
< 3000 mg/L
< 150 mg/L CaCO3
< 0.1 mg/L
< 0.05 mg/L
— Hydrogen Sulfide
< 20 mg/L
< 0.1 mg/L
PROCESS FLOW DIAGRAM
Feed water goes through sediment prefilters to remove particles.
If using antiscalant for hard water then it is injected before the prefilters, so the chemical is mixed with water more thoroughly.
High pressure pump feeds the prefiltered water into the membrane array. Inside the membranes, feed water is separated into purified water (permeate) and brine with retained impurities (concentrate).
Ecosoft RO systems feature built-in concentrate recycle, sending part of the concentrate back to the pump. Recycle flow control and drain flow control work to sustain the operating pressure and the recycle/waste ratio.
Operating pressure is variable within allowed range. Higher pressure produces higher permeate flow rate and/or recovery. Proper operating pressure and recycle/waste must be set up during commissioning.
Ecosoft RO system runs in a completely automated fashion. The system stops to standby when pure water tank is full. Automated membrane rinse occurs every time before standby, with preprogrammed intervals during standby and service.
If any of below conditions occur, the system switches off and displays failure alert:
low feed water pressure
high operating pressure
high permeate conductivity
phase or voltage failure
changing out expendable filters in pre-filter housings
chemical clean (CIP) the RO membranes when signs of membrane scaling or fouling arise; those include lower permeate flow rate or higher permeate conductivity 10% or more; normally, CIP lasts a few months before another CIP is required
if CIP fails to restore membrane flux, the membrane elements need to be replaced;
whenever an extended downtime is to happen, the membranes should be rinsed and soaked in preservative solution
Carefully read the instruction before operating the unit.
Only use piping of equal or larger diameter than the RO system's inlet and outlet ports. Avoid long runs of small diameter pipe.
Only use equal or larger diameter point-of-entry filters to provide maximum influent water flow rate. 2,5×10 size filters only have up to 1-2 m³/h capacity (5-10 gpm) and should not be used for this Ecosoft RO system.
Membranes are shipped in original packaging and must be installed before operating the system. O-ring seals on the membranes must be on the feed water side of the pressure vessel.
Remove plastic wraps from filters before installing them in pre-filter housings.
Make sure feed water is supplied to the system at required pressure before starting up the system.
Check Lovato protection relay when connecting power to the cabinet. Red light or flashing green light signals phase failure or abnormal voltage conditions as per instruction.
Do not use brass, iron, or copper pipe for permeate plumbing.
During first run, concentrate flow rate, recycle flow rate, and the operating pressure must be adjusted with the flow control valves. The operating pressure must not exceed 12 bar. The ratio of permeate flow rate to drain flow rate must not exceed 0.75.
It is advisable to supply influent water using a feed water tank and pump, and to deliver permeate using permeate tank and pump.