The Ecosoft FPC 2162CE125 filter is intended to reduce contents of hydrogen sulfide in water. The filter is commonly used for objects with capacity below 2.65 m3/h (5.3 m3/h in case the Ecosoft FK or FU filters are applied before).
The filter represents a durable vessel filled with high-quality CENTAUR® catalytic carbon (Calgon Carbon Corporation, USA), and is completed with a multifunction control valve.
CENTAUR® has catalytic properties and is capable of oxidizing hydrogen sulphide to form harmless and odourless compounds.
Purified water will become transparent, extraneous taste and unpleasant smell will disappear.
Pure water purified to remove odour of rotten eggs.
Fully automatic and noise-free.
Durable and efficient operation for no less than 5 years*.
Low volume of discharge.
Quality guaranteed by the international CE and ISO certificates.
* Subject to proper operation and timely replacement of filter media.
Filter construction and operation
The main part is the filter vessel filled with high-quality CENTAUR® activated carbon. In the upper part of the vessel there is a control valve with elements of the drainage-distribution system. The unit is connected to the cold water pipeline, sewage system and the electrical network to power the control valve.
When the filter media resources are exhausted, the filter automatically switches to regeneration mode. The reverse flow of water passes through the layer of media at high speed, washing out all impurities from the surface of the carbon, and is then discharged into the sewage system. After that, the filter is again ready to purify water. Regeneration occurs by raw untreated water.
The unique control valve is developed by Clack Corporation (USA). It provides filter’s independent service, keeps constant reserve of purified water and doesn’t require any special attention.
Who are the users?
The Ecosoft FPC 2162 CE125 filter will provide pure water for a commercial needs. The filter capacity is up to 2,65 m³ per hour. Installation is suitable for purifuing artesian and tap water.
Today, there are not so many effective solutions for removing hydrogen sulfide from water. The simplest and most effective method is the use of patented media CENTAUR. This media is an activated carbon treated with a special technology, as a result its surface acquires catalytic properties and becomes capable of oxidizing hydrogen sulfide to form safe and odourless compounds.
The filter is connected to the cold water supply. Pre-cleaned water enters the filter vessel filled with CENTAUR media, which effectively removes the odour of hydrogen sulfide. The purified water comes to the consumer through the central pipe.
Regeneration is carried out periodically to restore the properties of the media. The control valve switches the filter to regeneration mode at the specified time. For the consumer the convenience valve settings are programmed so that the filter is regenerated at a time when water consumption is not occurring. Water is passed through the filter with high speed reverse flow, which cleans the surface of the media material, washing out all impurities, and is discharged into the sewer system. After that, the system can again be used for water purification. For the regeneration of these filters raw water is used.
Thanks to the use of a multifunctional valve, the filter does not require constant attention. The only important task connected to maintenance for customer is timely stocking of the salt. It will ensure efficient regeneration of the filter media and thus durable filter service life and water quality.
If any problem arises, the valve will display a text message about the problem.
Nominal flow rate, m3/hour
Flow rate after Ecosoft FK or FU, m3/hour
Volume of CENTAUR® activated carbon, kg
Volume of quartz sand (base layer), kg
Water consumption for regeneration, m3/hour
Regeneration duration, min
Water volume per one regeneration, m3
Required level of water pre-treatment from sediments