The Ecosoft FPC 2162CE125 filter is intended to reduce contents of hydrogen sulfide in water. The filter is commonly used for objects with capacity below 2.65 m3/h (5.3 m3/h in case the Ecosoft FK or FU filters are applied before).
The filter represents a durable vessel filled with high-quality CENTAUR® catalytic carbon (Calgon Carbon Corporation, USA), and is completed with a multifunction control valve.
CENTAUR® has catalytic properties and is capable of oxidizing hydrogen sulphide to harmless and odorless compounds.
Purified water will become transparent, extraneous taste and unpleasant smell will disappear.
Pure water purified from the odor of rotten eggs.
Fully automatic and noise-free.
Durable and efficient operation during no less than 5 years*.
Low volume of discharge.
Quality guaranteed by the international CE and ISO certificates.
* Subject to proper operation and timely replacement of filter media.
Filter construction and operation
The main part is filter vessel filled with high-quality CENTAUR® activated carbon. In vessel upper part there is a control valve with elements of the drainage-distribution system. The unit is connected to the cold water pipeline, sewage system and the electrical network to power the control valve.
When the resource of the filter media is exhausted, the filter automatically switches to the regeneration mode. The reverse flow of water passed through the layer of media at high speed, washing out all impurities from the surface of the carbon, and is discharged into the sewage system. After that, the filter is again ready to purify water. Regeneration occurs by raw untreated water.
The unique control valve is developed by Clack Corporation (USA). It provides filter’s independent service, keeps constant reserve of purified water and doesn’t require any special attention.
Who are the users?
The Ecosoft FPC 2162 CE125 filter will provide pure water for a commercial needs. The filter capacity is up to 2,65 m³ per hour. Installation is suitable for purifuing artesian and tap water.
Today, there are not so many effective solutions for removing hydrogen sulfide from water. The simplest and most effective method is the use of patented media CENTAUR. This media is an activated carbon treated with a special technology, as a result its surface acquires catalytic properties and become capable to oxidize hydrogen sulfide into safe and odorless compounds.
The filter is connected to the cold water supply. Pre-purified water enters the filter vessel filled with CENTAUR, which effectively removes the odor of hydrogen sulfide. The purified water through the central pipe moves to the consumer.
Regeneration is carried out periodically to restore the properties of the media. The control valve switch the filter in regeneration mode at the specified time. For the consumerces convenience valve settings are programmed so that the filter is regenerated at a time when water consumption is not occurring. Water is passed through the filter with high speed reverse flow, which cleans the surface of the media, washing out all impurities, and is discharged into the sewer system. After that, the system can again be used for water purification. For the regeneration of these filters raw water is used.
Thanks to the use of a multifunctional valve, the filter does not require constant attention.
If any problem arises, the valve will inform about the problem at the display with a text message.
Nominal flow rate, m3/hour
Flow rate after Ecosoft FK or FU, m3/hour
Volume of CENTAUR® activated carbon, kg
Volume of quartz sand (base layer), kg
Water consumption for regeneration, m3/hour
Regeneration duration, min
Water volume per one regeneration, m3
Required level of water pre-treatment from sediments