The Ecosoft FPA 2162 CE125 filter is intended to reduce chlorine content and its toxic compounds in water, as well as organic impurities causing a yellowish water colour. The filter is applicable for objects with capacity below 2.65 m3/h (5.3 m3/h in case the Ecosoft FK or FU filters are applied before).
The filter represents a durable vessel filled with high-quality activated carbon FILTRASORB® 300 (Calgon Carbon Corporation, USA), and is completed with a multifunction control valve.
The unique control valve is developed by Clack Corporation (USA). It provides filter’s independent service, keeps constant reserve of purified water and doesn’t require any special attention.
Fully automatic and noise-free.
Service life of the filter media is no less than 1.5 years.
Low volume of water consumption for regeneration thanks to light weight of the media.
Quality guaranteed by the international CE and ISO certificates.
Activated carbon is well known to be an effective sorbent with a large active surface. It is an indispensable component of every first aid kit. At the same time, activated carbons are also widely used in many industries to remove various impurities. In water treatment, activated carbon is used to reduce contents of chlorine, chlorination by-products and organic matter typical for surface waters.
The filter is connected to cold water supply. Water enters the filter vessel and goes through the layer of the filter media, which effectively reduces sediment. Purified water is delivered to the consumer through the riser pipe of the filter vessel.
When the filter is exhausted, it automatically switches to regeneration mode in order to regenerate the operational characteristics of the filter media.
At the prescribed time the control valve shifts the system into regeneration mode. For the consumer’s convenience, the system is regenerated during times when water is not being consumed. During the regeneration the filter is backwashed at high speed, the water stirs and cleans the surface of activated carbon, washing out all the impurities, and then is discharged into the drain. After this the system can be used for water purification again. Untreated feed water is used for the regeneration.
Thanks to the use of a multifunctional valve, the filter does not require constant attention. The only important task connected to maintenance for customer is timely stocking of the salt. It will ensure efficient regeneration of the filter media and thus durable filter service life and water quality.
If any problem arises, the valve will display a text message about the problem.
Operational capacity, m3/h
Capacity after the Ecosoft FK or FU filters, m3/h
Volume of activated carbon FILTRASORB® 300, kg
Volume of quartz sand (base layer), kg
Water consumption during regeneration, m3/h
Regeneration duration, min
Water volume per one regeneration, m3
Required level of water pre-treatment from sediment particles